Before...Cyprus electrician standard
After...Limassol Electrician 24/7 standard
Consumer unit upgrade for a customer in Limassol. Replacing the old miss match MCB's with new 30ma RCBO's plus installing type 2 SPD (surge protection device).
Before...typical Cyprus electrician standard! An incorrect mix of MCB's that are not type tested for this board and a typical unsafe incorrectly fitting busbar and no care in how the cable connections are made and with no torque settings
After...correctly chosen RCBO's and SPD with MCB, insulated busbar, care and attention to wiring connection and correct torque screwdriver settings in accordance with manufactures stated tolerances
What is an SPD (Surge protection device) and why you should have one installed as standard when upgrading/replacing your fuse board in Cyprus. With the lighting storms that we get in Cyprus and with almost all rural homes being supplied by overhead exposed cables (TT supply), Limassol Electrician 24/7 is now fitting as standard SPD's either at the main switch RCD or within the consumer unit.