Limassol Electrician 24/7 called to a beautiful house in Fasoula, Limassol, problems with a 3 pole (3 phase) circuit breaker that was tripping inside the property at the ground floor fuse board (main distribution consumers unit).
Upon testing we found this breaker was the main supply MCB supplying another consumer unit in the swimming pool pump room. This consumer unit was found to be in very poor and unsafe condition, the cover was missing and no where to be found, and clear signs of water staining on many of the MCB's (miniature circuit breakers).
Our final report will recommend a full rebuild of the roof for the pump room to ensure water never enters any of the electrical equipment for the swimming pool, plus a full rebuild of this 3 phase board to comply with the latest regulations of BS: 7671.
This is how we found it, a recent 3 phase fuse board installation by a "Cyprus master electrician", incorrect circuit breakers with NO RCD PROTECTION as required by current wiring regulations. And just look at the junction box this electrician made, 3 phase connections leading to the fuse board in connectors!
Full rebuild of the mess we found and removal of the ready terribly unsafe junction box connections. Now all the circuit wiring leads directly into the rebuilt fuse board and each circuit is protected by a 30ma RCBO circuit breaker as required by safety wiring regulations. Also installed is a 4 pole SPD (surge protection device).
For all your circuit protection needs, single phase and 3 phase, indoor consumer units and outside main switch, professional wiring upgrades to comply with current wiring safety regulations, call Limassol Electrician 24/7.
Limassol MTB Adventures - Sponsored by Limassol Electrician 24/7 Cyprus
Electric vehicle charger wallbox installations in Paphos by English speaking licensed electrician. All makes of EV, Toyota, Nissan, BMW, Tesla.
âCall the British trained EV charger Electrician in Paphos, telephone 94449354
Electric vehicle wallbox installations, Limassol, Paphos, Larnaca, Nicosia. Call the Limassol EV electrician on 94449354, email [email protected]
Main RCD switch next to your electricity meter needs regular inspections and testing by a licensed and qualified Limassol Electrician. So many of these older style units that we come across on a daily basis are faulty and potentially very dangerous. Call Limassol Electrician 24/7 today for an electrical inspection, tel 94449354
Electric heated towel rails offer several benefits, making them a popular choice for bathrooms and even other areas of the house. Here are some of the advantages:
When considering an electric heated towel rail, it's essential to choose a model that suits your specific needs and the size of your bathroom. Additionally, professional installation ensures safety and optimal performance. Call Limassol Electrician 24/7 today for an installation appointment.
If you are experiencing no power problems due to your main electricity switch shutting down try these solutions to establish the possible cause.
Call Cyprus Electrician 24/7 for expert advice and service for no power faults caused by your main RCD switch not resetting.
Many Huawei Sun2000 and other makes of Photovoltaic solar installations in Cyprus have been installed without the necessary data cable to connect the system to the internet. If you want to monitor and control your solar PV system from the Fusion Solar app on your smartphone, you must first have an PV experienced qualified Internet electrician run a Cat5e data cable to your inverter. In our experience its much better to connect the WLAN-FE Smart Dongle to the internet via an Ethernet cable, connecting to a suitable router via RJ45 port. For further assistance, contact the Internet electrician in Limassol at Limassol Electrician 24/7.
You can now pay for all your professional electrician needs in Cyprus with Bitcoin. Contact the Bitcoin electrician at Cyprus Electrician 24/7, Limassol.
Contact the Bitcoin 24 hour emergency electrician service in Limassol Cyprus, WhatsApp 94449354